Steam Turbine - TR m600
Steam Turbine TR m600 is used both with and without a gear. The advantage of this steam turbine type is the possibility of using more rows of blades. Steam turbine blades can be regulated by either mechanical or electronic regulator.
Steam turbine TR m600 consists of a frame welded together, where the small steam turbine, generator, pump, second gear, oil kit and oil tank can be found. The rotor of steam turbine is placed between two plain bearings. The rotor shaft is connected to the gear with a flexible link. Impermeability of the steam system is assured through a special contact valve, through which steam can vent.
1. steam entrance
2. steam exit
3. turbine case
4. mechanical regulator
5. running machine
6. base frame
Working placement of the steam turbine
This types of steam turbines automatically control the rotations of the shaft, based on the requirements of the running machine. In the case of mechanical drive, the output pressure of steam is not regulated.
This type of steam turbine TR m600 already save money in Sugarcane Factory in Edfu Egypt.
|For Mechanical drive||Yes|
|For powering generator||Yes|
|With an integrated gear||No|
|Input steam pressure max. [MPa]||6.0|
|Input temperature of steam max. [°C]||450|
|Output steam pressure max. [MPa]||0.9|
|Generator output max. [kW]||1,200|
|Generator rotations [rpm]||5000|