Steam Turbine - TR HI 150
TR HI 150 is a special machine for reducing the pressure of water, designed for extremely low currents of steam with a high requirement for safe, mechanical run with a high effectiveness.
The steam turbine case together with the el. generator stator forms a unit without a gear and without secondary rotating parts. The turbine wheel is connected to a high frequency el. generator. Impermeability of the steam system is assured through a contact valve. The turbine includes a complete oil system for supplying the grease.
1. steam entrance
2. steam exit
3. turbine case
4. base frame
5. High frequency generator
Running a steam turbine together with a steam reducing station
The steam turbine automatically reduces the pressure of steam from higher value to the required lower value. The generator electricity output is tied to the amount of steam.
On the schema above you can see the set up of Steam Turbine. The priority is with generating heat, in our case steam in the boiler for the current technology. The steam travels to the steam divider and then is reduced to the required low pressure at the steam reduction station. The Steam Turbine is connected in parallel to the reduction station in order to increase the efficiency of the whole heating circulation.
|For Mechanical drive||No|
|For powering generator||Yes|
|With an integrated gear||No|
|Input steam pressure max. [MPa]||4.0|
|Input temperature of steam max. [°C]||420|
|Output steam pressure max. [MPa]||0.6|
|Generator output max. [kW]||80|
|Generator rotations [rpm]||30000|